In the maintenance of the heating system includes: repair of leaks in pipes, appliances, fixtures, replacement of individual sections of heaters, faucets, insulation of pipes and equipment that are in open or cool places, expansion tanks, removal of pipeline reverse slope, installation of additional fixtures, and strengthening the existing hangers and hooks, setting taps in places where you can not solve reverse slope or air pockets (bags); Troubleshooting site management and boiler, inspection and replacement of faulty instrumentation, washing, cleaning and painting of expansion tanks, Sump, elevators, stop and control valves, air collectors, flushing of the system (annually at the end of heating season) and its regulation. When major repairs shift pipelines, replace or repair furnaces, water heaters, pumps, control units, boilers. Receiving repaired the system in operation beginning with the inspection and verification of compliance with its technical documentation on the repairs. Learn more at this site: Professor of Internet Governance. After flushing the system spends its hydraulic test. Experiencing the system during the warm season. For more information see this site: kevin ulrich. Before the test, open all valves and taps on the air collector. For connecting a hydraulic press and fill it with water through the back line.
Filling produce slowly so the air is completely removed from the system. Once in the valves of the air tanks will be water, close them and create pressure in the hydraulic press system in excess of 1.25 times the working. After 5 min. pressure drop should not exceed 0.02 MPa. After testing and commissioning of a selection committee make preservation of the system before the heating season. For this system is filled with purified water from the thermal network. Regulate the heating system at the beginning of the heating season as follows. Open the valve on the input to the heating system of the building and serves coolant from the thermal network pipes and heaters.
Then pass along the main pipelines, check the heating of the lower points of all risers. On the overheated riser cover taps, gradually attaining the same temperature Return water in all risers. Then seek uniform heating radiators on the floors, covering the taps of overheated equipment. The temperature is determined in the middle section of the radiator, farthest from the riser. The thermal test is considered complete if the room temperature deviates from the estimated no more than 1 2 C.